Loading in 2 Seconds...
Loading in 2 Seconds...
C НЕ MTRADE ESTONIA OÜ. GAS PUMPING AGGREGATE 6.3 MW HIGHLY EFFICIENT LOW EMISSION N О x and CO. Our goal : Pure environment. Savings Reliability. GAS PUMPING AGGREGATE 6,3 MW MULTI-FUEL GAS TURBINE ENGINE D – 336 MODERNIZATION OF GAS COMBUSTION UNIT OF ANY VOLUME
Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.
CНЕMTRADE ESTONIA OÜ GAS PUMPING AGGREGATE 6.3 MW HIGHLY EFFICIENT LOW EMISSIONNОxandCO
Our goal:Pure environment SavingsReliability
GAS PUMPING AGGREGATE 6,3 MW MULTI-FUEL GAS TURBINE ENGINE D – 336 MODERNIZATION OF GAS COMBUSTION UNIT OF ANY VOLUME FOR TURBINES, BOILERS AND INDUSTRIAL FURNACES HIGHLY EFFICIENT LOW EMISSIONNОxandCO SUPPLY OF EQUIPMENT DESIGN AND CONSTRUCTION RECONSTRUCTION AND MODERNIZATION WARRANTY AND SERVICE
GAS PUMPING AGGREGATE TYPE 6,3 МW . Supplied kit includes: • gas turbine engine D-336; • set of mounting parts; • set of spare parts; • operational documentation; • set of instruments; • container for storage and transportation of gas turbine actuator; • automatic control system; • diagnostics system; • installation of flushing gas-air line; • service and training of personnel during warranty period; • set of endoscopes.
GAS TURBINE ENGINE D-336 • Quantity ofGTEtype D-336 in usage - 154 pieces • The total operating time ofGTE D-336 - more than2 500 000 hours Gas Turbine Engines D-336 are used as a gas compressor drive, gas liftingandcrude oil pumping aggregatesof capacity 6,3 МW, and also as a power plants generator drives.Engines successfully operate in different climatic zones at an ambient temperature from -60 ° C to +50 ° C at altitudes above sea level up to 2000 m.
GAS TURBINE ENGINED-336TECHNICAL CHARACTERISTICS • Engine Modification: D-336-1, D-336-2, D-336-2Т* • Nominal Power(MCA, H=0), kW6300 • Frequency of rotor rotation of power turbine, min-1 8200** • Fuel - gaseous *** (naturaloroil gas) • Effective Efficiency, % not less then 31 • Overall dimensions, mm3932,5x1068,0x1227,4 • Weight, kg 1470 * Maintaining the power up to t = +25 °С.** If necessary, modifications may be made for GTEwith rotational frequencies 5000 or 3000 rev/min, and besidesD-336-1 –left rotation, D-336-2, D-336-2Т – right rotation.*** Upon customer request, engines can be converted to run on liquid fuel – kerosene of RT, TS-1 or similar fuels of foreign production.
GAS TURBINE ENGINED-336 MAIN FEATURES • High fuel efficiency at constant price increases for natural gas • Solution of problems of reducingCO andNOx in combustion products • Minimal investment in new construction, reconstruction and modernization • High reliability and dependability (total operating time - 2 500 000 hours) • Low cost of maintenance • High level of maintainability without dismantling with possibility of a modular repair • High degree of automation • Warranty and maintenance service for the entire period of operation
High efficiencyHigh reliabilityHigh effectivenessin all modes of 10-110% Reduced temperature modeUnified, simple,technological EFFECTIVENESS OF A NEW GENERATION OF GAS BURNER Low emission: NOx- no more than 25ppm СО- no more than 8 ppm
Testing results for modernized combustion chamber of turbine type GTK-10-4 (power 10 MW) 13
USING MODERNIZED COMBUSTION CHAMBERIS THE BASE TO EXTEND MOTOR RESOURCE AK REGENERATOR CC HPT LPT Diagram of the temperature distribution 1- specifications data(passport); 2 – Real data of measurement AK- axial-compressor compressor,CC – chamber of combustion, HPT – high pressure turbine,LPT – Low pressure turbine 14
RESULTS OF MODERNIZATION • Natural gas savings 10-15% • Reduction of pollution: • NОxnot more than 10÷50 мg/м3 (25 ppm); • CO not more than 5÷10 мg/м3 (8 ppm) • Increasing project value of turbine up to 30% • Wide range of turbine power regulation with high gas savings and low NOx and CO from 10 to 120% • Fast recoupment of investment 10-24 months • High level of uniformity of temperature field in gas combustion zone and vibration decrease prolong service life of turbine (primarily a catalyst). • Opportunity to fulfill short term tasks (from 1 to 30 days)reduces losses from downtime. • No necessity in purchasing new turbines and accessory equipment.
Process of gas combustion in turbine Before modernization New Generation Burner Thank you for Your attention! CНЕMTRADE ESTONIA OÜ Madara 31-21, Tallinn, 10613, Estonia Tel: +372660-10-50, fax: +372 660-10-50 E-mail: firstname.lastname@example.org CONSORTIUM FOR CONSTRUCTION AND RECONSTRUCTION OF HYDROELECTRIC POWER STATIONS 105 Swetland Lane 2-nd floor, West Wyoming, PA 18644, USA Tel:+1 570301-90-67, fax:+1 570300-18-41 e -mail:: consnikre @ gmail.com