TIS Climate Control. Course 20 Minutes Test 10 Minutes. TIS Training Program 2012 , Rev 1.1 www.tissmarthome.com. How TIS can control climate?. BY Infrared Control. By Interlocked Relay. By 0-10 Volt Output. By Relay ON/OFF. Thermostat / Temperature sensors. Climate Control.
Course 20 Minutes
Test 10 Minutes
TIS Training Program 2012 , Rev 1.1 www.tissmarthome.com
Many of TIS items came with built in temperature sensor like the ES-10F and AC-10G also some has temp sensor input like the HVAC Module.
The panel can read the temp sensor from itself or from any device , also it can calculate the average of many devices in the same room
Energy Servant with 10 functions
Celling mount device , can save up to 200 Infrared codes
with 6 Infrared transmit lenses , it can send 360 degree of infrared codes
It has different other functions like motion sensor and saving energy timer
IR Emitter with current sensor
Free locate small device, can save up to 200 Infrared codes
with external Infrared 1.5 meter wire and transmitter head.
Panel Addition with IR Emitter
Small size , installed behind the panel in the wall, can save up to 64 Infrared codes, can be connected to door contact to make saving energy logic.
Need extra external Infrared 1.5 meter wire and transmitter head.
HVAC control with 6 relays each 3 Amps
Include relay control for compressor, heater, auxiliary output, beside the 3 speed fan control (Low, Medium, High). Recommended to use this relay in most of (apartments, offices, hotel) project.
Power Relay 12 channels each of 10 Amps
Good relay, fast and low noise , can be interlocked to be used for FCU Fan speed control (Low, Medium, High). (can not control compressor or heater relay)
Recommended to use this relay in most of (apartments, offices, hotel) project.
By Interlocked Relay.
Addition 3 Channels each of 3 Amps
Small size , installed behind the panel in the wall box, fast and low noise , small size can be interlocked to be used for FCU fan speed or HVAC control.
Recommended to use this relay in (all rooms to replace the normal thermostat)
VAV control with 0-10 volt output
It has also 0-10 Volt output to control VAV (Dampers opening and closing volume)
For Floor heater
Can use any of TIS relay Module
We need a relay channel for each room with floor heater electronic valve.
High Load Air condition
Need to use strong relay like Relay 8ch 16A
We need strong relay to turn ON/OFF such type of Air condition unit .
Use Cat5e cable to connect between all your Panels, relay and other TIS devices