MPSB: 2GEV project. TE-EPC Group Meeting 26 of June 2009. Jean-Paul Burnet. MPSB: Actual configuration. Main problems: Not enough voltage due to 5% tolerance on network and commutation voltage drop Input transformer Irms above the limit of 1882A (2300A)
Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.
TE-EPC Group Meeting 26 of June 2009
Alfa is fully opened but still the current does not rump-up as wanted
Irms (1.2s) = 2300A
Irms (1.2s) = 1700A
Power pulse increase
3 transformers 2500MVA and 3 rectifiers as those used in POPS needed