ISC Learning center. E.Lighting - Dardo Plus system 4 - Portable Testing tool: Syscon. The Syscon kit. Control device Syscon User guide External power supply: 230 V AC input / 9 V DC out Strap Cable of external connexion. Functioning: What can we check?.
Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.
E.Lighting - Dardo Plus system
4 - Portable Testing tool: Syscon
Control device Syscon
External power supply: 230 V AC input / 9 V DC out
Cable of external connexion
Indication than the luminaire is a three-hour duration.
Green LED switch OFF:1-hour duration.
Mains present:Yellow LED:
Indication than the luminaire detected has the recharging power supply line present.
Yellow LED switch OFF:no recharging power supply line not present.
Tube OFF:Red LED:
Indication if the luminaire has the tube OFF.
Red LED switch OFF:tube ON.
Tens - units display:
Red tens and units displays indicate the decimal place assigned to the luminaire detected.
Luminaires numbers range from 00 to 99 (100 numbers).
The full stop remains displayed and indicates the presence of the display power supply.
Red LED ON:light tube OFF
Red LED OFF:light tube ON
Yellow LED ON:light power supply line present
Yellow LED OFF:light power supply line absent
Green LED ON: Dardo circuit set up for 3 h
Green LED OFF: Dardo circuit set up for 1 h
Three-colour battery LED:
Green LED:indicates the presence of the recharging network.
Orange LED:indicates normal battery functioning.
Red LED:indicates that the battery autonomy for the Syscon is low and gives the operator advance warning to turn it OFF.
OFF: Press Off to have equipment OFF.
No effect when the recharging network is present.
ON: Press On to have equipment in battery mode. No effect when the recharging network is present, the equipment stays ON.
RESET: Reset all types of command, restoring the stand by conditions (two full stops).
Start the acquisition from the connected line.
Detect the luminaire data and save it in the memory.
Give the data of each luminaire reading it from memory.
Test the luminaires connected to the Dardo Line.
To end the TEST condition for the luminaire connected to the Dardo Lines.
Restore the initial condition (two full stop).
To turn OFF the luminaire if the luminaires have the line not present condition.
In the REST MODE and line absent condition, restore the normal emergency condition by turning ON the luminaires.
For problems: check for any incorrect connections with the energy sources.