1 / 14

# can a heat pump replace a boiler - PowerPoint PPT Presentation

(Press F5 if not auto start). Can a Heat pump replace a boiler?. (arrow-down or mouse-click). Not without a bit of thought. Maximum efficiencies are unlikely to be achieved without a few changes to the system. Let us consider a Condensing boiler circuit. Example. Heat output approximates

Related searches for can a heat pump replace a boiler

I am the owner, or an agent authorized to act on behalf of the owner, of the copyrighted work described.

## PowerPoint Slideshow about 'can a heat pump replace a boiler' - paul2

Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.

- - - - - - - - - - - - - - - - - - - - - - - - - - E N D - - - - - - - - - - - - - - - - - - - - - - - - - -
Presentation Transcript
Can a Heat pump replace a boiler?

(arrow-down or mouse-click)

Not without a bit of thought.

Maximum efficiencies are unlikely to be achieved without a few changes to the system

Example

Heat output approximates

to average (mean)

flow-return temperature

Flue losses

10 – 15%

85 – 90% energy

to water

56°C

56°C

(Flow-rate 1)

50°C

rt = 12°

Boiler

44°C

44°C

http://www.heatpumps.co.uk/heatpumpcalculator.html

Low return temperature helps condensing- increases efficiency

Example

Heat output approximates

to average (mean)

flow-return temperature

Keeping flow temperature low

increases energy efficiency

Same heat output

As previous slide

53°C

53°C

(Flow-rate x 2)

50°C

rt = 6°

Heat

Pump

47°C

47°C

Electrical input (relative to heat output) can vary considerably

http://www.heatpumps.co.uk/heatpumpcalculator.html

but the average temperature is unchanged.

How did we achieve these temperature changes?

In our example we have doubled the water flow rate.

Remember, our heat (kW) is the same in every example.

Note: - To increase the flow-rate, the pipe diameter is likely to have to be bigger so that pumping power is not increased.

(pump energy is an energy loss).

Heat (kW) = Flow rate (lit/sec) x 4.2 x rt

Heat output approximates

to average (mean)

flow-return temperature

(Repeat of previous slide)

Simple formula for heat, water flow and temperature difference

Keeping flow temperature low

increases energy efficiency

Same heat output

As previous slide

Example

53°C

53°C

(Flow-rate x 2)

50°C

rt = 6°

Heat

Pump

47°C

47°C

Electrical input (relative to heat output) can vary considerably

http://www.heatpumps.co.uk/heatpumpcalculator.html

You might think that the heat transfer is better when there is a large flow-return temperature difference.

However, it all depends on how fast the heat is taken away.

i.e. it depends in the water flow rate.

If the heat transfer (kW) is constant, and the flow rate is doubled, then the temperature difference between the flow and return is halved.

Our heat pump prefers this, it ‘sees’ a lower flow temperature.

How can we reduce the working temperature further? is a large flow-return temperature difference.

Increase the size of the radiator.

A bigger radiator will emit more heat, so the temperatures are ‘dragged down’ to a lower temperature.

Now with a bigger radiator is a large flow-return temperature difference.

All temperatures now 12° lower.

Rule of thumb: - 1° drop in water

temperature can result in about 2.5%

improvement in system efficiency.

A bigger emitter system

reduces the working

temperatures.

This increases the COP

significantly.

Keeping flow temperature low

increases energy efficiency

Same heat output but

at lower temperature

Example

41°C

41°C

(Flow-rate x 2)

38°C

rt = 6°

Heat

Pump

35°C

35°C

(Doubling the radiator area can reduce the mean temperature from 50° to about 38°C)

Could we have done anything else? is a large flow-return temperature difference.

If we insulate the house more, then less heat is needed, this can reduce the water temperatures required.

This therefore increases the energy efficiency of the heat pump.

What else could reduce the temperature? is a large flow-return temperature difference.

Now with underfloor heating is a large flow-return temperature difference.

Better still :-

underfloor heating

designed for

low temperatures

Keeping flow temperature low

increases energy efficiency

Example

Pipes in floor screed

36°C

36°C

(Flow-rate x 2)

43°C

rt = 6°

Heat

Pump

30°C

30°C

Note : - In general, tiles or slabs on screed give better results than wood.

http://www.heatpumps.co.uk/heatpumpcalculator.html

So, we now have an efficient heat pump system. is a large flow-return temperature difference.

It took a few changes

But the increase in energy efficiency makes the long term energy savings worthwhile

Don’t forget to check your heat pump’s settings. A simple adjustment to reduce the water temperature in the heating system will save energy.

showing approximate implications to the efficiency (COP)

It should be noted that the above are mid-winter temperatures.

With weather-compensation, the temperatures can be reduced

at milder times, thus increasing the COP.