System Sizing. Proper System Design. Load Calculation Equipment Selection Duct Layout Branch runs Terminations Start ups Customer checks. The Next Step. Room By Room Load Calculation. Kwik-Way. www.spacepak.com Contractor assistance. Load Calculation.
Altitude Pressure = 14.696x(1-6.87535E-06xA)
Where: A = altitude in feet
Corrected CFM =
Where: a=pressure at altitude, b=specific CFM, c=entering air temperature
Model # SpacePak # Mfr SEER Matched capacity AEU
AC024X1222 345719 ESP-2430V+TDRLUXAIRE, 11.10 * 22600 * $171*
AC024X1222 345540 ESP-2430D+TDRLUXAIRE, 10.90 * 22200 * $171*
Let’s do a house!
Central Location – Out of Direct Living Area
Each 2”run will provide between 1700-2000 btu at a run length of 10’-20’
3 restrictor sizes
15%, 30% and 50%
Living room = 3 full runs
Family room = 5 full runs
How about the Dining room?
Needs two outlets but gain is only 2800 btu.
Use 2 30% restrictors on both runs. = 2800 btu
Runs must total 19 full open for 3642D – 850 CFM to get ESP to 1” and 1.5” W.C.
Will this pull
Difficult to keep up on 100° days
Space Pak’s 6 row coil
Humidity control built in
Size for the worst dayWe Never Undersize