BS 8519- Code of Practise Selection and Installation of Fire Resistant Power and Control Cable Systems for Life Safety and Fire Fighting Applications- Code of Practise. Name of the speaker Jobtitle Location – Date www.drakauk.com. B.S. 8519:2010.
Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.
BS 8519- Code of PractiseSelection and Installation of Fire Resistant Power and Control Cable Systems for Life Safety and Fire Fighting Applications- Code of Practise
Name of the speaker
Location – Date
evacuation systems are required to operate both in evacuation and fire –fighting phases.
For means of escape 30 minutes fire survival time, cables shall:
For Fire Fighting 120 minutes fire survival time cables shall
BSEN 50200 + water Spray
Test is integrated But:
Impact is indirect
Water is applied via a sprinkler head not a pressure hose
Based on the BS 7846 test but is Integrated.
Constant temperature attack at 842°C
Direct mechanical impact = 10 N
Pressure Water jet (6.3mm hose,12.5l/m) during final 5 minutes of test - to simulate fire hose
Firetufpowerplus utilises additional fire barriers and new Halogen Free, Low Smoke material technology, compared to B.S.7846 F2 cable FTP. It has conventional wire armour design, and complies with B.S.7846, and B.S.8491 to the 120 minute rating (category 3)
FTP120 has been independently tested by LPCB and has a full approval from BASEC
Thank you for your attention