Common Monitoring and Reporting Errors. Louis Nichols Clean Air Markets US EPA March 2007. Generator Replacement.
PowerPoint Slideshow about ' Common Monitoring and Reporting Errors' - lee-drake
An Image/Link below is provided (as is) to download presentation
Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.
If an electric generator less than 25 MWe is replaced with another electric generator which has a nameplate of greater than 25 MWe, then the previously non-affected unit may become an Acid Rain Program/CAIR unit.
Test the accuracy of each fuel flowmeter once every four fuel flowmeter QA operating quarters, unless the meter qualifies for test deadline extensions. The deadline may be extended, one quarter at a time up to a maximum of 20 calendar quarters from the last test.
For non-QA quarters in which the fuel flowmeter is used less than 168 hours; or
If the optional fuel flow-to-load test is performed and passed each quarter (Part 75, Appendix D, section 2.1.7).
For orifice-, nozzle-, and venturi-type flowmeters perform the primary element inspection (PEI) once every 12 calendar quarters and perform the transmitter or transducer accuracy tests once every four fuel flowmeter QA quarters.
The interval between transmitter or transducer calibrations may be extended, up to 20 calendar quarters if the fuel flow-to-load test is performed and passed or if there are not enough fuel flowmeter QA quarters.
The PEI may be extended up to 20 calendar quarters only if the fuel flow-to-load test is performed and passed. (Note: Appendix D, section 2.1.7 requires that the PEI and transmitter or transducer be performed in the same quarter.)
For some monitoring plans such as subtractive stacks, multiple stacks, and others, the Part 75 Policy Manual may contain valuable reporting as well as CEMS quality assurance information – Tip : Use searchable version
Electronic Data Reporting (EDR) Instructions
EDR Instructions contain specific reporting information for all units – Tip: Use searchable version