WHY SAFETY. BEING A HUMAM , MORAL RESPONSIBILITY FOR ALL OF US TO HELP OTHERS, SOCITY AND ENVIORNMENT. Electrical Safety Guidelines. safety guidelines for our valued consumers. Guidelines for Domestic consumers Guidelines for Commercial consumers Guidelines for Industrial consumers
BEING A HUMAM ,
MORAL RESPONSIBILITY FOR
ALL OF US
TO HELP OTHERS,
SOCITY AND ENVIORNMENT.
NOT ONLY INDIVIDUAL
ALSO AFFECT SOCIETY AND NATION
Indian Electricity Act 1956:
To Whom to be Reported:
Officer In-charge of Local Police
Telephonic information Within 24 hr.
Written report Within 48 hr.
RULE 44-A OF IRE 1956:
IF ANY ACCIDENT OCCURRED IN CONNECTION WITH GENERATION, TRANSMISSION, SUPPLY OR USE OF ENERGY IN OR IN CONNECTION WITH, ANY PART OF ELECTRIC SUPPLY LINES OR OTHER WORKS OF ANY PERSON AND THE ACCIDENT RESULTED IN OR IS LIKELY TO HAVE RESULTED HUMAN BEING OR ANIMAL LIFE SUCH PERSON OR ANY AUTHORIZED PERSON OF THE STATE ELECTRICITY BOARD OR SUPPLIER NOT BELOW THE RANK OF J E OR EQUIVALENT SEND TO THE INSPECTOR TELEGRAPHIC REPORT WITHIN 24 HOURS OF THE OCCURRENCE OF FATAL ACCIDENT AND WRITTEN REPORT IN THE FORM SET OUT IN ANNEXURE XIII WITHIN 48 HOURS OF THE KNOWLEDGE OF OCCURANCE OF FATAL AND ALL OTHER ACCIDENTS .
PENALITY FOR BREACH OF RULE
WHERE, IN CONTRAVENTION OF RULE 44-A ANY PERSON RESPONSIBLE FOR GENERATION, TRANSMISSION CONVERSION, DISTRIBUTION, SUPPLY OR USE OF ENERGY FAILS TO REPORT INSPECTOR AND AUTHORIZED CONCERED,THE OCCURRENCE OF ACCIDENT, SUCH PERSON SHALL BE PUNISHABLE WITH THE FINE WHICH MAY EXTENT TO THREE HUNDRED RUPEES.
Communication circuits coming under the influence of electric field of high voltage power line experience extraneous induction, which may introduce noise in communication equipment and cause danger to the equipment and persons handling them.
Therefore, it is very essential that whenever power liens and communication lines pass close to each other suitable measures are taken. Approval of PTCC (Power Tele communications Co-ordination Committee) may be obtained.
Further, while crossing the telecom lines, the following points may be observed :
UP TO 33 KV SYSTEM
TELECOM LINE AND GUARD WIRE
-:1.22 METER ( 4’ )
TELECOM LINE AND CONDUCTOR OUP TO 11 KV
:1.525 METER ( 5’ )
TELECOM LINE AND CONDUCTOR OF 33 KV
:1.1.830 METRE ( 6’ )
The ground clearance of the guard wire and strength of the supports on either side of the road have to be considered in installing a cradle guard at the road crossings. The supports on either side of the road on which the cradle guard terminates are earthed separately and the line should not cross at an angle less than 60°.