Loading in 5 sec....

Power Generation Using Multi Component Working FluidsPowerPoint Presentation

Power Generation Using Multi Component Working Fluids

- By
**jiro** - Follow User

- 71 Views
- Uploaded on

Download Presentation
## PowerPoint Slideshow about ' Power Generation Using Multi Component Working Fluids' - jiro

**An Image/Link below is provided (as is) to download presentation**

Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.

- - - - - - - - - - - - - - - - - - - - - - - - - - E N D - - - - - - - - - - - - - - - - - - - - - - - - - -

Presentation Transcript

### Power Generation Using Multi Component Working Fluids

P M V Subbarao

Professor

Mechanical Engineering Department

Indian Institute of Technology Delhi

Synthesis of More Appropriate Working Fluids……

Flue gases

External

Irreversibility-1

1

1

C

6

1kg

8

Steam

5

7

T

6

4

5

External

Irreversibility-2

2

3

f

3

e

Cooling water

S

s

External Irreversibilities with Rankine cycle

Irreversible Heat transfer process : Rankine CycleWorking fluid water – Best performance at high pressure

Low pressure and low temperature region

- Heat and mass balance program
- Optimal bleed pressure &

Fig 2 Layout of modern Coal fired power plant

0.3783 m3/ kg

Exit at higher velocity

Kinetic Energy loss

12.65 m3/ kg

Location of condensation process in a Low pressure steam turbine

(Source Alstom )

Moisture Loss

For example, a long, full speed rotor blade, operating in a non-reheat cycle, may involve wetness levels of about 15% at

exhaust.

Without suitable counter-measures this can result in extreme tip-erosion (illustrated in Fig).

Erosion of a long last stage blade

( Source Alstom )

Source of Energy Vs Working Fluid

- The overall efficiency of a thermodynamic conversion cycle is a consequence of ;
- the energy potential of the source-sink combination, of internal inefficiencies (losses in turning machinery, in regenerators,etc.) and
- of losses from irreversible heat transfer from a source and to a sink.
- The latter depends mostly on the levels of matching of the apparent heat capacities of the working fluid, source and sink.

- In principle, a divergence in the thermal behaviour between a working fluid and a source or sink can be counteracted by using complex cycle configurations such as evaporation at multiple pressure levels in modern combined cycles or condensation at 2 or 3 decreasing temperatures in cogenerative systems.

T a working fluid and a source or sink can be counteracted by using complex cycle configurations such as evaporation at multiple pressure levels in modern combined cycles or condensation at 2 or 3 decreasing temperatures in cogenerative systems.0C

300

250

200

150

100

50

Two Phase Fluid

Energy Recovery from Hot GasSelection of Another Working Fluid along with Water !!! a working fluid and a source or sink can be counteracted by using complex cycle configurations such as evaporation at multiple pressure levels in modern combined cycles or condensation at 2 or 3 decreasing temperatures in cogenerative systems.

- The fluid generally has lower boiling temperature than water.
- Lower freezing point and high stability temperature.
- Higher latent heat and low liquid specific heat or near vertical saturated liquid line so that most of the heat is added during change of phase without the need for the complexity of regenerative feed heating to ‘Carnotize the cycle’ to realize high cycle efficiency.
- Small specific volume and low viscosity.
- The fluid should to be non-corrosive, non-flammable, non-toxic and safe to use.
- Good availability and low cost.

T-S and T-X DIAGRAMS : Binary Components a working fluid and a source or sink can be counteracted by using complex cycle configurations such as evaporation at multiple pressure levels in modern combined cycles or condensation at 2 or 3 decreasing temperatures in cogenerative systems.

Mixtures as Working Fluids a working fluid and a source or sink can be counteracted by using complex cycle configurations such as evaporation at multiple pressure levels in modern combined cycles or condensation at 2 or 3 decreasing temperatures in cogenerative systems.

- Any single component working fluid, due to pinch, approach point limitations and a constant boiling point, cannot cool the gases to low temperature.
- Single component fluid can recover only about 15-20 % of the energy is that recovered by a two phase fluid.
- Multiple pressure systems could recover more energy, but added the complexity of the system and cost.
- The main characteristic is that the boiling of working fluid occurs over a range of temperatures.
- By virtue of varying boiling point, two component working fluid is able to "match" or run parallel to the gas (source) cooling temperature line while recovering energy and hence the final exit gas temperature can be low.
- The condensation of two component working fluid also occurs over a range of temperatures and hence permits additional heat recovery in the condensation system.

- The condenser pressure can be much higher in two component fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .
- Thermo-physical properties of mixture can also be altered by changing the concentration of one component.
- This helps to recuperate or regenerate energy in the condensation system.
- Modifications to the condensing system are also possible by varying the mixture concentration and thus more energy can be recovered from the exhaust gases.
- Expansion in turbine can give a saturated vapor in two component fluid cycle compared to wet steam.
- Conventional equipment such as steam turbines can be used in two component fluid cycle.

Rankine Cycle Vs Novel Cycle fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .

- Binary working fluid -- A mixture of two fluids.
- Variable temperature Boiling.

- Varying concentration of binary fluid in different parts of the cycle.
- Varying thermodynamic properties.

- Internal Recovery of Heat.
- Energy recovery from a one stream of working fluid to another stream of working fluid.

- 15 -- 25% improvement in efficiency.
- Less Irreversibility.

Brief History fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .

- The technology is the creation of Dr. Alexander Kalina, a Russian scientist.
- He left a high position in Soviet Union 30 years ago to come to US.
- Formed Exergy Inc. to develop and commercialize an advanced Thermodynamic Cycle.
- 1993, General Electric signed an agreement with Exergy for a world wide exclusive licensing rights to use the technology for combined cycle systems in 50 MW to 150 MW range.
- GE and Exergy working on a combined cycle plant that will operate on an overall efficiency of 62%.

Simple Kalina Cycle fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .

The pump pressurized the saturated liquid (5) which is leaving from the condenser and it is sent in to the high temperature recuperator (6).

The liquid takes off the heat from the two phase dead vapour (3).

The pressurized hot liquid (sub-cooled state) enters (1) into the vaporizer where the liquid is converted in to vapor (2) by utilizing the latent or sensible heat of the hot source (1s-2s).

The saturated vapor (2) from the vaporizer is expanded in the turbine up to its condenser pressure.

The two phase mixture after giving a part of it’s latent heat to the incoming liquid (4) enters in to the condenser, where cooling water enters (1w), takes away all the heat available in the two-phase mixture, and leaves at higher temperature (2w).

The saturated liquid is pressurized in the pump and the cycle repeats.

T-S and T-X DIAGRAMS fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .

Ammonia water cycle modeling fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .

- The mathematical models for Ammonia water cycle are constructed using the theory of thermodynamics.
- The whole system is divided into many components namely vaporizer, steam turbine, condenser, high temperature recuperator etc.
- According to the characteristic construction of each component, appropriate assumptions are introduced.
- Steady State Steady Flow Models are developed.

Vaporizer fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .

The heat transfer rate fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .QV(W) between the source and the working fluid is calculated by

Optimization fluid cycle, and the cooling water temperatures do not impact the power output of the turbine .

- In this case, efficiency of the cycle is considered as the objective function to be optimized.
- The Ammonia water cycle has four variables.
- Fraction of ammonia (x)
- Turbine inlet pressure (P3)
- Heat source inlet temperature T1S
- Heat source outlet temperature T3S.
- The cycle performance depends on the values for these four variables that are free to change during optimization.
- Each combination of the eight values represents a unique operating condition of the cycle.
- Searching for optimum values for these variables are the task of this optimization work.
- Consequently, the objective function to be maximized can be written as,

The objective function is solved with the help of most power full

optimization methodology ‘Monte Carlo’.

First law efficiency of the cycle is defined as

Variation of first law efficiency at different steam inlet conditions of simple

Saturation Pressure of Rankine Cycle (bar)

Effect of variation in fraction of ammonia at the evaporator inlet on first law efficiency

Condenser pressure in the Ammonia water cycle largely depends on cooling water inlet temperature and fraction of Ammonia in the Ammonia water mixture.

For the same cooling water inlet temperature, decreasing the Ammonia mass fraction at the condenser inlet will reduce the condenser pressure and it will leads to larger expansion process in the turbine and hence more power output and higher efficiency

The Kalina Cycle : Nine Components inlet on first law efficiency

Modern Kalina Cycle inlet on first law efficiency

Effect of variation in fraction of ammonia at the evaporator inlet on first law efficiency

The following modifications are suggested for the proposed Ammonia water cycle when compared to KCS 34.

1.Super heater is added in the cycle to utilize the superheated steam at low temperature and pressure.

The saturated vapor from the separator is superheated in the super heater before entering the steam turbine.

2.The additional feed water is included in the system, which utilize the sensible heat of low grade to heat the sub-cooled water coming it from the condenser of an Ammonia water cycle

Kalina Cycle with Subcooler inlet on first law efficiency

Effect of turbine inlet pressure on first law efficiency inlet on first law efficiency

The Superheat Kalina Cycle inlet on first law efficiency

Comparison of Exergy destruction in various components of the Ammonia water cycles

Download Presentation

Connecting to Server..