1 / 14

# 11. Stability of Closed-Loop Control Systems - PowerPoint PPT Presentation

11. Stability of Closed-Loop Control Systems. In this chapter, we analyze the stability characteristics of closed-loop system and present several useful criteria for determining whether a system will be stable. - Closed-loop transfer function for set-point changes.

I am the owner, or an agent authorized to act on behalf of the owner, of the copyrighted work described.

## PowerPoint Slideshow about ' 11. Stability of Closed-Loop Control Systems' - bond

Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.

- - - - - - - - - - - - - - - - - - - - - - - - - - E N D - - - - - - - - - - - - - - - - - - - - - - - - - -
Presentation Transcript

• In this chapter, we analyze the stability characteristics of closed-loop system and present several useful criteria for determining whether a system will be stable.

- Closed-loop transfer function for set-point changes

Figure 11.1. Effect of controller gains on closed-loop response to a unit step change in set point

• Open loop stable (Self-regulating) process:

the stable process without feedback control

• Definition of stability(BIBO Stability):

An unconstrained linear system is said to be stable if the output response is bounded for all bounded inputs. Otherwise it is said to be unstable.

Example

Figure 11.2. A liquid storage system which is not self-regulating

Transfer function relating liquid level h to inlet flow rate qi

For a step change of magnitude M0,

Taking the inverse Laplace transform gives the transient response,

Since this response is unbounded, we conclude that the liquid storage system is open-loop unstable (or non-self-regulating) since a bounded input has produced an unbounded response.

However, if the pump in Fig.11.2 were replaced by a valve, then the storage system would be self-regulating.

In Chapter 10

where, GOL = GcGvGpGm

For set-point changes, Eq. (11-5) reduces as

where, m  n for physical realizability

From Eq. (11-6) the poles are also the roots of the following equation which is called as the characteristic equation:

1 + GOL = 0 plays a decisive role in determining system stability

If R(s) = 1/s and there are no repeated poles, then

Thus, one of the poles is a positive real number, c(t) is unbounded.

If pkis ak+jbk, imaginary part causes the oscillatory response and with a positive real part, then the system is unstable.

• General Stability Criterion

The conventional feedback control system is stable if and only if all roots of the characteristic equation are negative or have negative real parts. Otherwise, the system is unstable.

Figure 11.3. Stability regions in the complex plane for roots of the characteristic equation

• Note) The same characteristic equation occurs for both load and set-point changes since the term, 1 + GOL. Thus, if the closed-loop system is stable for load disturbance, it will also be stable for set-point changes.

11.2 Routh Stability Criterion to closed-loop response.

• Concept: an analytical technique for determining whether any roots of polynomial have positive real parts

• Method:

Characteristic Equation: ansn+ an-1sn-1+ ··· +a1s + a0 = 0 (an>0)

1) all the coefficients an , an-1, ··· a0 must be positive.

(if any coefficient is negative or zero, then the system is unstable.)

2) construct Routh array

where, to closed-loop response.n is the order of characteristic equation,

All of the elements in the left column of the Routh array are positive

⇒ only valid if characteristic equation is in polynomial of s (no time delay).

⇒ if system contain time delays use Pade approximation.

Note) A exact stability analysis of system containing time delays will be treated in the frequency analysis.

11.3 Direct Substitution Method to closed-loop response.

• Concept: Substituting s = jw into the characteristic equation → find a stability unit such as the maximum value of Kc .

Example

Use the direct-substitution method to determine Kcm for the system with the characteristic equation given by.

10s3 + 17s2 + 8s + 1 + Kc = 0 (11.9)

Solution

Substitute s = jw and Kc = Kcm into Eq.(11-9):

-10jw3- 17w2 + 8jw + 1 + Kcm = 0

or (1 + Kcm- 17w2) +j(8w-10w3) = 0 (11.10)

Equation (11.10) is satisfied if both real and imaginary parts of (11.10) are identically zero:

1 + Kcm- 17w2 = 0, 8w-10w3 = 0

Therefore, w = 0.894  Kcm = 12.6

• Thus, we conclude that to closed-loop response.Kc < 12.6 for stability.

• w = 0.894 indicates that at the stability limit (where Kc = Kcm = 12.6), a sustained oscillation occurs that has a frequency of w = 0.894 radians/min if the time constants have units of minutes.

(Recall that a pair of complex roots on the imaginary axis, , results in an undamped oscillation of frequency w.)

• The corresponding period P is P = 2p/0.894 = 7.03 min.

11.4 Root Locus Diagrams to closed-loop response.

In the design and analysis of control systems, it is instructive to know how the roots of the characteristic equation change when a particular system parameter such as controller gain changes.

• A root locus diagram provides a convenient graphical display of this information.

Example)

Consider a feedback control system that has the following open-loop transfer function.

Plot the root locus diagram for 0 Kc 40

Solution: The C. E. is ( to closed-loop response.s + 1)(s + 2)(s + 3) + 2Kc = 0.

Figure 11.5. Root locus diagram for third-order system.

From the above root locus diagram,

• The closed-loop system is underdamped one for Kc > 0.2.

• The closed-loop system is unstable for Kc > 30.

• Disadvantage of root locus analysis.

→ cannot handle time delay. Thus, use the Pade approximation.

→ require iterative solution of the nonlinear and nonrational characteristic equation (but not easy).

From C. E.

These roots are shown in Fig. 11. 6

Figure 11.6. Root location for underdamped second-order system