With a breathtaking view of the Diamond Head and Koko Head craters, Kahala Hotel & Resort appeared to be picture perfect, but beneath the surface of the renowned hotel was a failing pipe system causing regular disruption to the resort’s operations.
Download Policy: Content on the Website is provided to you AS IS for your information and personal use and may not be sold / licensed / shared on other websites without getting consent from its author.While downloading, if for some reason you are not able to download a presentation, the publisher may have deleted the file from their server.
Where life interacts with infrastructure.
Nu Flow Protects Resort Hotel with Retrofitted Storm Line
With a breathtaking view of the Diamond Head and Koko Head craters, Kahala Hotel & Resort appeared to be
picture perfect, but beneath the surface of the renowned hotel was a failing pipe system causing regular disruption
to the resort’s operations.
Project: Clean and line the underground storm line using Nu Flow’s trenchless, cured-in-place structural drain liner.
Customer: The Kahala Hotel & Resort, located in
the Kahala district of Honolulu, Hawaii. The hotel is
known as one of Hawaii’s most luxurious and secluded
beachfront resorts, with 338 rooms and suites, five
stylish restaurants and a world-class spa.
System: 180 feet of 8” clay and PVC storm drain pipe
running from the hotel to a manhole and directly to the
Situation: Roots had intruded the storm line causing
backups and leaks into the restaurant when it rained.
Compounding the problem, portions of the drain pipe
were below the high-tide water level, which lead to sea
water exfiltration from the pipe into the surrounding
grounds of an area that hosted up to six weddings a day.
Solution: While the tide was out, Nu Flow first cleaned the
storm line to remove buildup and roots that had intruded
through the pipe. Once complete, Nu Flow inserted a
Pull-in-Place structural liner in the existing pipe using
the patented Nu Flow process. Nu Flow lined from the
building, underneath the wedding ceremony area and to
the manhole, sealing all leaks and preventing roots from
reentering the sewer. Nu Flow completed the retrofit
without the need to dig a trench to access the pipe,
preserving the picture-perfect landscape and hardscape.
Using trenchless technology, Nu Flow
cleaned the storm drain pipe system and
installed a structural liner to seal all leaks
and prevent root intrusion.
Root intrusion is common in storm and sewer lines. Whether you are experiencing problems now or are interested
in preventing the inevitable failure of your plumbing system, Nu Flow is available to restore your peace of mind.
North America: 1-800-834-9597 | International: 1-905-433-5510
email@example.com | www.nuflowtech.com
p/n 379 v1.2